Powerlink PSCR Maintaining reliability of supply between Clare South and Townsville South
In this section
In this section
- Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply to the Rockhampton area
- Powerlink Queensland PACR addressing the secondary systems condition risks at Woree Substation
- Powerlink Queensland PACR to maintain power transfer capability and reliability of supply at Ross Substation
- Maintaining a reliable Upper Tumut substation
- Managing safety and environmental risks from corrosion on Line 959/92Z
- Managing the Risk of Corrosion between Murulan and Dapto on Line 8
- Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply to the Brisbane Metropolitan area
- Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply at Townsville South Substation
- Managing the Risk of Corrosion between Vales Point and Sydney North on Line 22
- Powerlink PSCR Maintaining reliability of supply between Clare South and Townsville South
- SA Energy Transformation PACR
- SA Power Networks publishes Distribution Annual Planning Report
- Powerlink Queensland PACR Maintaining power transfer capability and reliability of supply at Bouldercombe Station
- Powerlink Summary Queensland PADR Maintaining reliability of supply to Rockhampton
- Powerlink PACR to address the secondary systems condition risks at Belmont substation
- Powerlink PACR to address the secondary systems condition risks at Abermain Substation
- TransGrid PSCR Managing Sydney East substation’s asset risks
- Powerlink Project Assessment Conclusions Report (PACR) to address the secondary system condition risks at Palmwoods Substation
- Project Assessment Conclusions Report – Addressing the secondary systems condition risks at Tarong Substation
- Project Specification Consultation Report - Maintaining power transfer capability and reliability of supply at Woree Substation
Powerlink has recently published a ‘Project Specification Consultation Report’ (PSCR) to maintain reliability of supply between Clare South and Townsville South.
The 132kV network between Collinsville and Townsville was developed in the 1960s and 1970s to supply mining, commercial and residential loads in north Queensland. Its main function today is to provide connections to Invicta Mill and Clare South substations, and to support power transfers in the area, including from renewable generation.
Both the coastal and inland single circuit lines between Townsville South and Clare South substations are exhibiting signs of advanced degradation on the majority of structures. The decay of the buried steel grillage foundations of the inland Townsville South to Clare South line and the tower leg/foundation interfaces on the coastal line pose an increasing risk of tower failure during storm events.
Powerlink has identified four credible network options to address the risks to supply arising from the condition of ageing transmission lines between Clare South and Townsville South. Two options involve life extension of the existing lines and two options involve a combination of life extension of the coastal line, combined with substitution of the inland line with a second transformer at Strathmore Substation.
All proposed network options extend the life of the 132kV network between Clare South and Townsville South through to 2040, at which time the area’s 275kV lines are likely to have reached the end of their technical service life, providing an opportunity to review the configuration of the complete network in the area.
Indicative proposed initial network capital costs required by December 2022 range between $36.6 million and $55 million in 2018/19 prices.
In accordance with the requirements of the Rules, a summary of the PSCR is made available on the AEMO website. A copy of the ‘Project Specification Consultation Report’ can be obtained from the Powerlink website on the RIT-T Consultations page or by emailing email@example.com.
To assist and encourage submissions from the broader community and stakeholders in this area, the public consultation period for the PSCR has been extended beyond the original closure date of 15 March 2019.
Submissions on the PSCR are now required by the closing date of 18 April 2019.
Any enquiries in the first instance should be directed to:
Manager Network and Alternate Solutions
PO Box 1193
VIRGINIA, QLD 4014
Tel: (+617) 3860 2328
- Summary of PSCR (209 KB, pdf)