Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply to the Rockhampton area
In this section
In this section
- Maintaining compliance with performance standards applicable to Haymarket substation secondary systems
- Maintaining a reliable Static Var Compensator at Lismore
- Powerlink Queensland Project Specification Consultation Report - Maintaining power transfer capability and reliability of supply at Lilyvale
- Powerlink Queensland - Project Assessment Draft Report - Maintaining reliability of supply at Kamerunga Substation
- Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply to the Rockhampton area
- Powerlink Queensland PACR addressing the secondary systems condition risks at Woree Substation
- Powerlink Queensland PACR to maintain power transfer capability and reliability of supply at Ross Substation
- Maintaining a reliable Upper Tumut substation
- Managing safety and environmental risks from corrosion on Line 959/92Z
- Managing the Risk of Corrosion between Murulan and Dapto on Line 8
- Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply to the Brisbane Metropolitan area
- Powerlink Queensland - Project Assessment Conclusions Report - Maintaining reliability of supply at Townsville South Substation
- Managing the Risk of Corrosion between Vales Point and Sydney North on Line 22
- Powerlink PSCR Maintaining reliability of supply between Clare South and Townsville South
- SA Energy Transformation PACR
- SA Power Networks publishes Distribution Annual Planning Report
- Powerlink Queensland PACR Maintaining power transfer capability and reliability of supply at Bouldercombe Station
- Powerlink Summary Queensland PADR Maintaining reliability of supply to Rockhampton
- Powerlink PACR to address the secondary systems condition risks at Belmont substation
- Powerlink PACR to address the secondary systems condition risks at Abermain Substation
Powerlink has recently published a ‘Project Assessment Conclusions Report’ (PACR) to maintain reliability of supply in the Rockhampton area.
The Egans Hill to Rockhampton transmission line is a 132kV double circuit line commissioned in 1963 that forms part of the connection between Powerlink’s Bouldercombe and Rockhampton substations. It provides a critical link into the Rockhampton Substation, which is a major injection point for the Rockhampton and surrounding area distribution network.
The transmission line between Egans Hill and Rockhampton is nearing the end of its technical service life, with the majority of structures on the transmission line exhibiting signs of degradation. Specifically, loss of the galvanising on members, the onset of early corrosion to nuts, bolts and hardware, and the decay of grillage foundations, all increase the risk of mechanical failure of components of the transmission line, particularly in storm and cyclonic conditions.
In accordance with the Regulatory Investment Test for Transmission (RIT-T), Powerlink published a Project Specification Consultation Report (PSCR) in September 2018, followed by the publication of the Project Assessment Draft Report (PADR) in January 2019. The PADR identified the preferred option, a staged life extension of the line, with Stage 1 to be completed by December 2020 and Stage 2 by December 2030, with a full rebuild by 2044. Both the PSCR and PADR invited submissions on credible non-network options, which could address the identified need. There were no submissions received in response to either the PSCR or PADR.
The outcomes of the economic analysis contained in the PACR remain unchanged from those published in the PADR. Consequently, the draft recommendation to implement the preferred option has been adopted without change as the final recommendation in the PACR.
The RIT-T project involves refitting and painting the northern section of the line and refitting without painting the southern section of the line by December 2020, at an estimated capital cost of $9.98 million in 2018/19 prices. Powerlink is the proponent of the proposed network project.
In accordance with the requirements of the Rules, a summary of the PACR has been made available on AEMO’s website. A copy of the PACR can be obtained from the Powerlink Website on the RIT-T Consultations page or by emailing firstname.lastname@example.org.
Any enquiries in the first instance should be directed to:
Manager Network and Alternate Solutions
PO Box 1193
VIRGINIA, QLD 4014
Tel: (+617) 3860 2328